Trade Name: AstroGrille
Intumescent Fire Grilles.
Fire Grilles tested to: BS EN 1634-2
Comprehensive range of sizes includes circular types.
For use in doors & wallsSuitable for mounting up to 1,000mm (1m) from floor level.
In excess of 30 or 60 minutes fire rating.
Vermin proof wire mesh 80% free area.
A durable ventilation grille which is easily mounted in doors & walls, and can provide in excess of 1/2 or 1 hour fire protection. Astroflame Fire Grille comprises of a moisture resistant intumescent core within a galvanized steel frame with vermin proof 6mm steel mesh fitted to both faces.
Suitable for fitting up to 1,000mm (1m) from floor level.
The design allows a free area of 80% approximately. See our air-flow table below for guidance.
All square and rectangular grilles are available to suit 30 minute or 60 minute fire rated applications.
Maximum single grille size is 600 x 600 mm or equivalent area.
Circular grilles are available in 100, 125, 150, 200, 225, 250 and 300mm diameter sizes and are 60 minute fire rated.
Air Flow Specifications
Free Air flow Table: ASTROFLAME Intumescent Fire Grilles.
Top row is width dimension. First column is Height dimension. Sizes in mm
To Order & Specify
Please contact us and quote the following - Quantity / Product Code / Product Description / Size
Test and Assessment Reports
Warrington Fire Research: Global Assessment C100767
Health and Safety
The product does not present any known health hazards during or after installation. Normal good industrial and personal hygiene practices should be observed. For further information on health and safety requirements please contact the technical team on: tel 01329 844 500 or email firstname.lastname@example.org
As part of our policy of ongoing improvements, we reserve the right to modify, alter or change product specifications without giving notice. Product illustrations are representations only. All information contained in this document is provided for guidance only, and as ASTROFLAME FIRESEALS LTD has no control over the installation methods of the products, or of the prevailing site conditions, no warranties expressed or implied are intended to be given as to the actual performance of the products mentioned or referred to, and no liability whatsoever will be accepted for any loss, damage or injury arising from the use of the information given of products mentioned or referred to herein.
The above information
to the best of our knowledge is true and accurate and based upon current
test data and is supplied for your guidance only. Customers should