Trade Name: Astro Duct Wrap
Intumescent Duct Wrap
Duct Wraps Tested to EN1366-3
European Fire Resistance Classification:
Wraps provide up to 2 Hr Integrity & Insulation to rectangular PVC ventilation ducting penetrations.
Simple & quick to install
Low profile design allows installation close soffit
Available to fit most common vent duct sizes
Only one wrap needed per penetration
Tested to EN1366-3 in Plasterboard using steel sleeves.
Duct wraps designed to provide simple and effective fire resistance for up to 2 hours to plastic vent ducting penetrations.
These duct wraps provide 120 minutes integrity and insulation protection having been fire tested in an Open/Open pipe/duct end configuration, to the most onerous requirements of EN 1366-3.
Installation is straight forward due to the four segment design and slide into the wall construction.
Supplied in various sizes to suit all common plastic vent duct dimensions.
Wraps are either 4mm or 8mm thick - check table below for available wrap sizes.
We do not supply steel sleeves ourselves but the dimensions for fabrication are shown below.
Astroflame Duct Wraps are either 4mm or 8mm thick - check table below for available wrap sizes.
To Order & Specify
Please contact us and quote the following - Quantity / Product Code / Product Description / Size
Test and Assessment Reports
Tested to EN1366-3
Health and Safety
The product does not present any known health hazards during or after installation. Normal good industrial and personal hygiene practices should be observed. For further information on health and safety requirements please contact the technical team on: tel 01329 844 500 or email firstname.lastname@example.org
As part of our policy of ongoing improvements, we reserve the right to modify, alter or change product specifications without giving notice. Product illustrations are representations only. All information contained in this document is provided for guidance only, and as ASTROFLAME FIRESEALS LTD has no control over the installation methods of the products, or of the prevailing site conditions, no warranties expressed or implied are intended to be given as to the actual performance of the products mentioned or referred to, and no liability whatsoever will be accepted for any loss, damage or injury arising from the use of the information given of products mentioned or referred to herein.
The above information
to the best of our knowledge is true and accurate and based upon current
test data and is supplied for your guidance only. Customers should