Trade Name: Astro Lumi Canopy
Fire Rated Luminaire Canopy
Fire Rated Luminaire Canopy (Fire Hood) suitable for use with suspended and modular ceilings.
Tested to BS 476 Part 23: 1987, Clause 5, 60 mins.
Complies with BS 476 Class "0" Building Regs.
Complies with BS 476 Part 6 - Fire Propogation and
Simple to install.
Can be fitted from above or below the ceiling.
Resistant to tear and abrasion.
Astroflame Luminaire Canopies stop the passage of fire and smoke, for up to 60 minutes, through luminaire light fittings in a fire rated ceiling.
Without the fire rated canopy in place, fire and smoke will penetrate the recessed light fitting in seconds and spread into the void or room above endangering lives and property.
The Astro Lumi Canopy provides 60 minutes fire protection (in a plasterboard ceiling) by completely containing the fire and smoke within the cover. In normal (non-fire) conditions the heat from the light fitting can dissipate through the canopy fabric.
The fire canopies are easy to fit from either side of the ceiling and need no additional supports. They can also ne easily removed and replaced for lighting maintenance.
Fully tested to BS Standard 476 part 20 & 23 clause 5. Astro Lumi Canopy also meets the requirements of class 0 materials.
To Order & Specify
Please contact us and quote the following - Quantity / Product Code / Product Description / size
Health and Safety
The product does not present any known health hazards during or after installation. Normal good industrial and personal hygiene practices should be observed. For further information on health and safety requirements please contact the technical team on: tel 01329 844 500 or email firstname.lastname@example.org
As part of our policy of ongoing improvements, we reserve the right to modify, alter or change product specifications without giving notice. Product illustrations are representations only. All information contained in this document is provided for guidance only, and as ASTROFLAME FIRESEALS LTD has no control over the installation methods of the products, or of the prevailing site conditions, no warranties expressed or implied are intended to be given as to the actual performance of the products mentioned or referred to, and no liability whatsoever will be accepted for any loss, damage or injury arising from the use of the information given of products mentioned or referred to herein.
The above information
to the best of our knowledge is true and accurate and based upon current
test data and is supplied for your guidance only. Customers should